Transformer

Pole-mounted single-phase transformer with center-tapped secondary. Note use of the ground conductor as one leg of the primary feeder.

A transformer is a device that transfers electrical energy from one circuit to another through inductively coupled conductors — the transformer's coils or "windings". Except for air-core transformers, the conductors are commonly wound around a single iron-rich core, or around separate but magnetically-coupled cores. A varying current in the first or "primary" winding creates a varying magnetic field in the core (or cores) of the transformer. This varying magnetic field induces a varying electromotive force (EMF) or "voltage" in the "secondary" winding. This effect is called mutual induction.

If a load is connected to the secondary, an electric current will flow in the secondary winding and electrical energy will flow from the primary circuit through the transformer to the load. In an ideal transformer, the induced voltage in the secondary winding (VS) is in proportion to the primary voltage (VP), and is given by the ratio of the number of turns in the secondary to the number of turns in the primary as follows:

$\frac{V_{S}}{V_{P}} = \frac{N_{S}}{N_{P}}$

By appropriate selection of the ratio of turns, a transformer thus allows an alternating current (AC) voltage to be "stepped up" by making NS greater than NP, or "stepped down" by making NS less than NP.

Transformers come in a range of sizes from a thumbnail-sized coupling transformer hidden inside a stage microphone to huge units weighing hundreds of tons used to interconnect portions of national power grids. All operate with the same basic principles, although the range of designs is wide. While new technologies have eliminated the need for transformers in some electronic circuits, transformers are still found in nearly all electronic devices designed for household ("mains") voltage. Transformers are essential for high voltage power transmission, which makes long distance transmission economically practical.

History

First steps: experiments with induction coils

What would become the "transformer principle" was revealed in 1831 by Michael Faraday in his demonstration of electromagnetic induction, but without recognition of its future role in manipulating EMF. The first "induction coils" to see wide use were invented by Rev. Nicholas Callan of Maynooth College, Ireland in 1836, one of the first researchers to realize that the more turns the secondary winding has in relation to the primary winding, the larger the increase in EMF. Induction coils evolved from scientists' and inventors' efforts to get higher voltages from batteries. Rather than alternating current (AC), their action relied upon a vibrating "make-and-break" mechanism that regularly interrupted the flow of direct current (DC) from the batteries. Between the 1830s and the 1870s, efforts to build better induction coils, mostly by trial and error, slowly revealed the basic principles of transformers. Efficient, practical designs did not appear until the 1880s,[1] but within a decade the "transformer" would be instrumental in the "War of Currents", and in seeing AC distribution systems triumph over their DC counterparts, a position in which they have remained dominant ever since.[1]

In 1876, Russian engineer Pavel Yablochkov invented a lighting system based on a set of induction coils where the primary windings were connected to a source of alternating current and the secondary windings could be connected to several "electric candles" (arc lamps) of his own design.[2][3] The coils used in the system behaved as primitive transformers.[2] The patent claimed the system could "provide separate supply to several lighting fixtures with different luminous intensities from a single source of electric power".

In 1878, the engineers of the Ganz Company in Hungary assigned part of its extensive engineering works to the manufacture of electric lighting apparatus for Austria-Hungary, and by 1883 made over fifty installations. It offered an entire system consisting of both arc and incandescent lamps, generators, and other accessories.[4]

Lucien Gaulard and John Dixon Gibbs first exhibited a device with an open iron core called a "secondary generator" in London in 1882, then sold the idea to the Westinghouse company in the United States.[5] They also exhibited the invention in Turin, Italy in 1884, where it was adopted for an electric lighting system.

Induction coils with open magnetic circuits are inefficient for transfer of power to loads. Various methods of adjusting the cores or bypassing magnetic flux around part of a coil were developed, since until about 1880 the paradigm for AC power transmission from a high voltage supply to a low voltage load was a series circuit. In practice, several coils with a ratio near 1:1 were connected with their primaries in series to allow use of a high voltage for transmission while presenting a low voltage to the lamps. The inherent flaw in this method was that turning off a single lamp affected all the others on the circuit, and many adjustable coil designs were introduced in an effort to accommodate this problematic characteristic of the series circuit.[6]

The birth of the first transformer

Stanley's 1886 transformer, a redesigned commercial version of the earlier Hungarian "ZBD" transformer

Between 1884 and 1885, Hungarian engineers Zipernowsky, Bláthy and Déri from the Ganz company in Budapest created the efficient "ZBD" closed-core model, which were based on the design by Gaulard and Gibbs. (Gaulard and Gibbs designed just an open core model) [7][8] They discovered that all former (coreless or open-core) devices were incapable of regulating voltage, and were therefore impracticable. Their joint patent described a transformer with no poles and comprised two versions of it, the "closed-core transformer" and the "shell-core transformer. In the closed-core transformer the iron core is a closed ring around which the two coils are arranged uniformly. In the shell type transformer, the copper induction cables are passed through the core. In both designs, the magnetic flux linking the primary and secondary coils travels (almost entirely) in the iron core, with no intentional path through air. The core consists of iron cables or plates. Based on this invention, it became possible to provide economical and cheap lighting for industry and households."[9] Zipernowsky, Bláthy and Déri discovered the mathematical formula of transformers: Vs/Vp = Ns/Np. With this formula, transformers became calculable and proportionable. Their patent application made the first use of the word "transformer", a word that had been coined by Ottó Bláthy.[10] George Westinghouse had bought both Gaulard and Gibbs' and the "ZBD" patents in 1885. He entrusted William Stanley with the building of a ZBD-type transformer for commercial use.[11] Stanley built the core from interlocking E-shaped iron plates. This design was first used commercially in 1886.[1]

Early developments and applications

Russian engineer Mikhail Dolivo-Dobrovolsky developed the first three-phase transformer in 1889. In 1891 Nikola Tesla invented the Tesla coil, an air-cored, dual-tuned resonant transformer for generating very high voltages at high frequency. Audio frequency transformers (at the time called repeating coils) were used by the earliest experimenters in the development of the telephone.

Basic principles

The transformer is based on two principles: firstly, that an electric current can produce a magnetic field (electromagnetism) and secondly that a changing magnetic field within a coil of wire induces a voltage across the ends of the coil (electromagnetic induction). Changing the current in the primary coil changes the magnitude of the applied magnetic field. The changing magnetic flux extends to the secondary coil where a voltage is induced across its ends.

An ideal step-down transformer showing magnetic flux in the core.

A simplified transformer design is shown to the left. A current passing through the primary coil creates a magnetic field. The primary and secondary coils are wrapped around a core of very high magnetic permeability, such as iron; this ensures that most of the magnetic field lines produced by the primary current are within the iron and pass through the secondary coil as well as the primary coil.

Induction law

The voltage induced across the secondary coil may be calculated from Faraday's law of induction, which states that:

$V_{S} = N_{S} \frac{\mathrm{d}\Phi}{\mathrm{d}t}$

where VS is the instantaneous voltage, NS is the number of turns in the secondary coil and Φ equals the magnetic flux through one turn of the coil. If the turns of the coil are oriented perpendicular to the magnetic field lines, the flux is the product of the magnetic field strength B and the area A through which it cuts. The area is constant, being equal to the cross-sectional area of the transformer core, whereas the magnetic field varies with time according to the excitation of the primary. Since the same magnetic flux passes through both the primary and secondary coils in an ideal transformer,[12] the instantaneous voltage across the primary winding equals

$V_{P} = N_{P} \frac{\mathrm{d}\Phi}{\mathrm{d}t}$

Taking the ratio of the two equations for VS and VP gives the basic equation[13] for stepping up or stepping down the voltage

$\frac{V_{S}}{V_{P}} = \frac{N_{S}}{N_{P}}$

Ideal power equation

The ideal transformer as a circuit element

If the secondary coil is attached to a load that allows current to flow, electrical power is transmitted from the primary circuit to the secondary circuit. Ideally, the transformer is perfectly efficient; all the incoming energy is transformed from the primary circuit to the magnetic field and into the secondary circuit. If this condition is met, the incoming electric power must equal the outgoing power.

Pincoming = IPVP = Poutgoing = ISVS

giving the ideal transformer equation

$\frac{V_{S}}{V_{P}} = \frac{N_{S}}{N_{P}} = \frac{I_{P}}{I_{S}}$

If the voltage is increased (stepped up) (VS > VP), then the current is decreased (stepped down) (IS < IP) by the same factor. Transformers are efficient so this formula is a reasonable approximation.

The impedance in one circuit is transformed by the square of the turns ratio.[12] For example, if an impedance ZS is attached across the terminals of the secondary coil, it appears to the primary circuit to have an impedance of $Z_S\!\left(\!\tfrac{N_P}{N_S}\!\right)^2\!\!$. This relationship is reciprocal, so that the impedance ZP of the primary circuit appears to the secondary to be $Z_P\!\left(\!\tfrac{N_S}{N_P}\!\right)^2\!\!$.

Detailed operation

The simplified description above neglects several practical factors, in particular the primary current required to establish a magnetic field in the core, and the contribution to the field due to current in the secondary circuit.

Models of an ideal transformer typically assume a core of negligible reluctance with two windings of zero resistance.[14] When a voltage is applied to the primary winding, a small current flows, driving flux around the magnetic circuit of the core.[14]. The current required to create the flux is termed the magnetizing current; since the ideal core has been assumed to have near-zero reluctance, the magnetizing current is negligible, although still required to create the magnetic field.

The changing magnetic field induces an electromotive force (EMF) across each winding.[15] Since the ideal windings have no impedance, they have no associated voltage drop, and so the voltages VP and VS measured at the terminals of the transformer, are equal to the corresponding EMFs. The primary EMF, acting as it does in opposition to the primary voltage, is sometimes termed the "back EMF".[16] This is due to Lenz's law which states that the induction of EMF would always be such that it will oppose development of any such change in magnetic field.

Practical considerations

Leakage flux

Leakage flux of a transformer

The ideal transformer model assumes that all flux generated by the primary winding links all the turns of every winding, including itself. In practice, some flux traverses paths that take it outside the windings.[17] Such flux is termed leakage flux, and results in leakage inductance in series with the mutually coupled transformer windings.[16] Leakage results in energy being alternately stored in and discharged from the magnetic fields with each cycle of the power supply. It is not directly a power loss (see "Stray losses" below), but results in inferior voltage regulation, causing the secondary voltage to fail to be directly proportional to the primary, particularly under heavy load.[17] Transformers are therefore normally designed to have very low leakage inductance.

However, in some applications, leakage can be a desirable property, and long magnetic paths, air gaps, or magnetic bypass shunts may be deliberately introduced to a transformer's design to limit the short-circuit current it will supply.[16] Leaky transformers may be used to supply loads that exhibit negative resistance, such as electric arcs, mercury vapor lamps, and neon signs; or for safely handling loads that become periodically short-circuited such as electric arc welders.[18] Air gaps are also used to keep a transformer from saturating, especially audio-frequency transformers in circuits that have a direct current flowing through the windings.

Effect of frequency

The time-derivative term in Faraday's Law shows that the flux in the core is the integral of the applied voltage.[19] Hypothetically an ideal transformer would work with direct-current excitation, with the core flux increasing linearly with time.[20] In practice, the flux would rise to the point where magnetic saturation of the core occurred, causing a huge increase in the magnetizing current and overheating the transformer. All practical transformers must therefore operate with alternating (or pulsed) current.[20]

Transformer universal EMF equation

If the flux in the core is sinusoidal, the relationship for either winding between its rms Voltage of the winding E, and the supply frequency f, number of turns N, core cross-sectional area a and peak magnetic flux density B is given by the universal EMF equation:[14]

$E={\frac {2 \pi f N a B} {\sqrt{2}}} \! \approx 4.44 f N a B$

The EMF of a transformer at a given flux density increases with frequency.[14] By operating at higher frequencies, transformers can be physically more compact because a given core is able to transfer more power without reaching saturation, and fewer turns are needed to achieve the same impedance. However properties such as core loss and conductor skin effect also increase with frequency. Aircraft and military equipment employ 400 Hz power supplies which reduce core and winding weight.[21]

Operation of a transformer at its designed voltage but at a higher frequency than intended will lead to reduced magnetizing current; at lower frequency, the magnetizing current will increase. Operation of a transformer at other than its design frequency may require assessment of voltages, losses, and cooling to establish if safe operation is practical. For example, transformers may need to be equipped with "volts per hertz" over-excitation relays to protect the transformer from overvoltage at higher than rated frequency.

Knowledge of natural frequencies of transformer windings is of importance for the determination of the transient response of the windings to impulse and switching surge voltages.

Energy losses

An ideal transformer would have no energy losses, and would be 100% efficient. In practical transformers energy is dissipated in the windings, core, and surrounding structures. Larger transformers are generally more efficient, and those rated for electricity distribution usually perform better than 98%.[22]

Experimental transformers using superconducting windings achieving efficiencies of 99.85%,[23] While the increase in efficiency is small, when applied to large heavily-loaded transformers the annual savings in energy losses are significant.

A small transformer, such as a plug-in "wall-wart" or power adapter type used for low-power consumer electronics, may be no more than 85% efficient, with considerable loss even when not supplying any load. Though individual power loss is small, the aggregate losses from the very large number of such devices is coming under increased scrutiny.[24]

The losses vary with load current, and may be expressed as "no-load" or "full-load" loss. Winding resistance dominates load losses, whereas hysteresis and eddy currents losses contribute to over 99% of the no-load loss. The no-load loss can be significant, meaning that even an idle transformer constitutes a drain on an electrical supply, which encourages development of low-loss transformers (also see energy efficient transformer).[25]

Transformer losses are divided into losses in the windings, termed copper loss, and those in the magnetic circuit, termed iron loss. Losses in the transformer arise from:

Winding resistance
Current flowing through the windings causes resistive heating of the conductors. At higher frequencies, skin effect and proximity effect create additional winding resistance and losses.
Hysteresis losses
Each time the magnetic field is reversed, a small amount of energy is lost due to hysteresis within the core. For a given core material, the loss is proportional to the frequency, and is a function of the peak flux density to which it is subjected.[25]
Eddy currents
Ferromagnetic materials are also good conductors, and a solid core made from such a material also constitutes a single short-circuited turn throughout its entire length. Eddy currents therefore circulate within the core in a plane normal to the flux, and are responsible for resistive heating of the core material. The eddy current loss is a complex function of the square of supply frequency and inverse square of the material thickness.[25]
Magnetostriction
Magnetic flux in a ferromagnetic material, such as the core, causes it to physically expand and contract slightly with each cycle of the magnetic field, an effect known as magnetostriction. This produces the buzzing sound commonly associated with transformers,[13] and in turn causes losses due to frictional heating in susceptible cores.
Mechanical losses
In addition to magnetostriction, the alternating magnetic field causes fluctuating electromagnetic forces between the primary and secondary windings. These incite vibrations within nearby metalwork, adding to the buzzing noise, and consuming a small amount of power.[26]
Stray losses
Leakage inductance is by itself lossless, since energy supplied to its magnetic fields is returned to the supply with the next half-cycle. However, any leakage flux that intercepts nearby conductive materials such as the transformer's support structure will give rise to eddy currents and be converted to heat.[27]

Equivalent circuit

Refer to the diagram below

The physical limitations of the practical transformer may be brought together as an equivalent circuit model (shown below) built around an ideal lossless transformer.[28] Power loss in the windings is current-dependent and is represented as in-series resistances RP and RS. Flux leakage results in a fraction of the applied voltage dropped without contributing to the mutual coupling, and thus can be modeled as reactances of each leakage inductance XP and XS in series with the perfectly-coupled region.

Iron losses are caused mostly by hysteresis and eddy current effects in the core, and are proportional to the square of the core flux for operation at a given frequency.[29] Since the core flux is proportional to the applied voltage, the iron loss can be represented by a resistance RC in parallel with the ideal transformer.

A core with finite permeability requires a magnetizing current IM to maintain the mutual flux in the core. The magnetizing current is in phase with the flux; saturation effects cause the relationship between the two to be non-linear, but for simplicity this effect tends to be ignored in most circuit equivalents.[29] With a sinusoidal supply, the core flux lags the induced EMF by 90° and this effect can be modeled as a magnetizing reactance (reactance of an effective inductance) XM in parallel with the core loss component. RC and XM are sometimes together termed the magnetizing branch of the model. If the secondary winding is made open-circuit, the current I0 taken by the magnetizing branch represents the transformer's no-load current.[28]

The secondary impedance RS and XS is frequently moved (or "referred") to the primary side after multiplying the components by the impedance scaling factor $\left(\!\tfrac{N_P}{N_S}\!\right)^2\!\!$.

Transformer equivalent circuit, with secondary impedances referred to the primary side

The resulting model is sometimes termed the "exact equivalent circuit", though it retains a number of approximations, such as an assumption of linearity.[28] Analysis may be simplified by moving the magnetizing branch to the left of the primary impedance, an implicit assumption that the magnetizing current is low, and then summing primary and referred secondary impedances, resulting in so-called equivalent impedance.

The parameters of equivalent circuit of a transformer can be calculated from the results of two transformer tests: open-circuit test and short-circuit test.

Types

A wide variety of transformer designs are used for different applications, though they share several common features. Important common transformer types include:

Autotransformer

An autotransformer with a sliding brush contact

An autotransformer has only a single winding with two end terminals, plus a third at an intermediate tap point. The primary voltage is applied across two of the terminals, and the secondary voltage taken from one of these and the third terminal. The primary and secondary circuits therefore have a number of windings turns in common.[30] Since the volts-per-turn is the same in both windings, each develops a voltage in proportion to its number of turns. An adjustable autotransformer is made by exposing part of the winding coils and making the secondary connection through a sliding brush, giving a variable turns ratio. [31]

Polyphase transformers

Three-phase step-down transformer mounted between two utility poles.

For three-phase supplies, a bank of three individual single-phase transformers can be used, or all three phases can be incorporated as a single three-phase transformer. In this case, the magnetic circuits are connected together, the core thus containing a three-phase flow of flux.[32] A number of winding configurations are possible, giving rise to different attributes and phase shifts.[33] One particular polyphase configuration is the zigzag transformer, used for grounding and in the suppression of harmonic currents.[34]

Leakage transformers

Leakage transformer

A leakage transformer, also called a stray-field transformer, has a significantly higher leakage inductance than other transformers, sometimes increased by a magnetic bypass or shunt in its core between primary and secondary, which is sometimes adjustable with a set screw. This provides a transformer with an inherent current limitation due to the loose coupling between its primary and the secondary windings. The output and input currents are low enough to prevent thermal overload under all load conditions – even if the secondary is shorted.

Leakage transformers are used for arc welding and high voltage discharge lamps (neon lamps and cold cathode fluorescent lamps, which are series-connected up to 7.5 kV AC). It acts then both as a voltage transformer and as a magnetic ballast.

Other applications are short-circuit-proof extra-low voltage transformers for toys or doorbell installations.

Resonant transformers

A resonant transformer is a kind of the leakage transformer. It uses the leakage inductance of its secondary windings in combination with external capacitors, to create one or more resonant circuits. Resonant transformers such as the Tesla coil can generate very high voltages, and are able to provide much higher current than electrostatic high-voltage generation machines such as the Van de Graaff generator.[35] One of the applications of the resonant transformer is for the CCFL inverter. Another application of the resonant transformer is to couple between stages of a superheterodyne receiver, where the selectivity of the receiver is provided by tuned transformers in the intermediate-frequency amplifiers.[36]

Audio transformers

Audio transformers are those specifically designed for use in audio circuits. They can be used to block radio frequency interference or the DC component of an audio signal, to split or combine audio signals, or to provide impedance matching between high and low impedance circuits, such as between a high impedance tube (valve) amplifier output and a low impedance loudspeaker, or between a high impedance instrument output and the low impedance input of a mixing console.

Such transformers were originally designed to connect different telephone systems to one another while keeping their respective power supplies isolated, and are still commonly used to interconnect professional audio systems or system components.

Being magnetic devices, audio transformers are susceptible to external magnetic fields such as those generated by AC current-carrying conductors. "Hum" is a term commonly used to describe unwanted signals originating from the "mains" power supply (typically 50 or 60 Hz). Audio transformers used for low-level signals, such as those from microphones, often included shielding to protect against extraneous magnetically-coupled signals.

Instrument transformers

Instrument transformers are used for measuring voltge,current, power and energy in electrical systems, and for protection and control. Where a voltage or current is too large to be conveniently measured by an instrument, it can be scaled down to a standardized low value. Instrument transformers isolate measurement and control circuitry from the high currents or voltages present on the circuits being measured or controlled.

Current transformers, designed for placing around conductors

A current transformer is a transformer designed to provide a current in its secondary coil proportional to the current flowing in its primary coil. [37]

Voltage transformers (VTs), also referred to as "potential transformers" (PTs), are used in high-voltage circuits. They are designed to present a negligible load to the supply being measured, to allow protective relay equipment to be operated at a lower voltages, and to have a precise winding ratio for accurate metering.[38]

Classification

Transformers can be classified in different ways:

• By power capacity: from a fraction of a volt-ampere (VA) to over a thousand MVA;
• By frequency range: power-, audio-, or radio frequency;
• By voltage class: from a few volts to hundreds of kilovolts;
• By cooling type: air cooled, oil filled, fan cooled, or water cooled;
• By application: such as power supply, impedance matching, output voltage and current stabilizer, or circuit isolation;
• By end purpose: distribution, rectifier, arc furnace, amplifier output;
• By winding turns ratio: step-up, step-down, isolating (equal or near-equal ratio), variable.

Construction

Cores

Laminated core transformer showing edge of laminations at top of unit.

Laminated steel cores

Transformers for use at power or audio frequencies typically have cores made of high permeability silicon steel.[39] The steel has a permeability many times that of free space, and the core thus serves to greatly reduce the magnetizing current, and confine the flux to a path which closely couples the windings.[40] Early transformer developers soon realized that cores constructed from solid iron resulted in prohibitive eddy-current losses, and their designs mitigated this effect with cores consisting of bundles of insulated iron wires.[5] Later designs constructed the core by stacking layers of thin steel laminations, a principle that has remained in use. Each lamination is insulated from its neighbors by a thin non-conducting layer of insulation.[32] The universal transformer equation indicates a minimum cross-sectional area for the core to avoid saturation.

The effect of laminations is to confine eddy currents to highly elliptical paths that enclose little flux, and so reduce their magnitude. Thinner laminations reduce losses,[39] but are more laborious and expensive to construct.[41] Thin laminations are generally used on high frequency transformers, with some types of very thin steel laminations able to operate up to 10 kHz.

Laminating the core greatly reduces eddy-current losses

One common design of laminated core is made from interleaved stacks of E-shaped steel sheets capped with I-shaped pieces, leading to its name of "E-I transformer".[41] Such a design tends to exhibit more losses, but is very economical to manufacture. The cut-core or C-core type is made by winding a steel strip around a rectangular form and then bonding the layers together. It is then cut in two, forming two C shapes, and the core assembled by binding the two C halves together with a steel strap.[41] They have the advantage that the flux is always oriented parallel to the metal grains, reducing reluctance.

A steel core's remanence means that it retains a static magnetic field when power is removed. When power is then reapplied, the residual field will cause a high inrush current until the effect of the remaining magnetism is reduced, usually after a few cycles of the applied alternating current.[42] Overcurrent protection devices such as fuses must be selected to allow this harmless inrush to pass. On transformers connected to long, overhead power transmission lines, induced currents due to geomagnetic disturbances during solar storms can cause saturation of the core and operation of transformer protection devices.[43]

Distribution transformers can achieve low no-load losses by using cores made with low-loss high-permeability silicon steel or amorphous (non-crystalline) metal alloy. The higher initial cost of the core material is offset over the life of the transformer by its lower losses at light load.[44]

Solid cores

Powdered iron cores are used in circuits (such as switch-mode power supplies) that operate above main frequencies and up to a few tens of kilohertz. These materials combine high magnetic permeability with high bulk electrical resistivity. For frequencies extending beyond the VHF band, cores made from non-conductive magnetic ceramic materials called ferrites are common.[41] Some radio-frequency transformers also have movable cores (sometimes called 'slugs') which allow adjustment of the coupling coefficient (and bandwidth) of tuned radio-frequency circuits.

Toroidal cores

Small toroidal core transformer

Toroidal transformers are built around a ring-shaped core, which, depending on operating frequency, is made from a long strip of silicon steel or permalloy wound into a coil, powdered iron, or ferrite.[45] A strip construction ensures that the grain boundaries are optimally aligned, improving the transformer's efficiency by reducing the core's reluctance. The closed ring shape eliminates air gaps inherent in the construction of an E-I core.[46] The cross-section of the ring is usually square or rectangular, but more expensive cores with circular cross-sections are also available. The primary and secondary coils are often wound concentrically to cover the entire surface of the core. This minimizes the length of wire needed, and also provides screening to minimize the core's magnetic field from generating electromagnetic interference.

Toroidal transformers are more efficient than the cheaper laminated E-I types for a similar power level. Other advantages compared to E-I types, include smaller size (about half), lower weight (about half), less mechanical hum (making them superior in audio amplifiers), lower exterior magnetic field (about one tenth), low off-load losses (making them more efficient in standby circuits), single-bolt mounting, and greater choice of shapes. The main disadvantages are higher cost and limited power capacity (see "Classification" above).

Ferrite toroidal cores are used at higher frequencies, typically between a few tens of kilohertz to a megahertz, to reduce losses, physical size, and weight of switch-mode power supplies. A drawback of toroidal transformer construction is the higher cost of windings. As a consequence, toroidal transformers are uncommon above ratings of a few kVA. Small distribution transformers may achieve some of the benefits of a toroidal core by splitting it and forcing it open, then inserting a bobbin containing primary and secondary windings.

Air cores

A physical core is not an absolute requisite and a functioning transformer can be produced simply by placing the windings in close proximity to each other, an arrangement termed an "air-core" transformer. The air which comprises the magnetic circuit is essentially lossless, and so an air-core transformer eliminates loss due to hysteresis in the core material.[16] The leakage inductance is inevitably high, resulting in very poor regulation, and so such designs are unsuitable for use in power distribution.[16] They have however very high bandwidth, and are frequently employed in radio-frequency applications,[47] for which a satisfactory coupling coefficient is maintained by carefully overlapping the primary and secondary windings.

Windings

Windings are usually arranged concentrically to minimize flux leakage
Cut view through transformer windings. White: insulator. Green spiral: Grain oriented silicon steel. Black: Primary winding made of oxygen-free copper. Red: Secondary winding. Top left: Toroidal transformer. Right: C-core, but E-core would be similar. The black windings are made of film. Top: Equally low capacitance between all ends of both windings. Since most cores are at least moderately conductive they also need insulation. Bottom: Lowest capacitance for one end of the secondary winding needed for low-power high-voltage transformers. Bottom left: Reduction of leakage inductance would lead to increase of capacitance.

The conducting material used for the windings depends upon the application, but in all cases the individual turns must be electrically insulated from each other to ensure that the current travels throughout every turn.[19] For small power and signal transformers, in which currents are low and the potential difference between adjacent turns is small, the coils are often wound from enamelled magnet wire, such as Formvar wire. Larger power transformers operating at high voltages may be wound with copper rectangular strip conductors insulated by oil-impregnated paper and blocks of pressboard.[48]

High-frequency transformers operating in the tens to hundreds of kilohertz often have windings made of braided litz wire to minimize the skin-effect and proximity effect losses.[19] Large power transformers use multiple-stranded conductors as well, since even at low power frequencies non-uniform distribution of current would otherwise exist in high-current windings.[48] Each strand is individually insulated, and the strands are arranged so that at certain points in the winding, or throughout the whole winding, each portion occupies different relative positions in the complete conductor. The transposition equalizes the current flowing in each strand of the conductor, and reduces eddy current losses in the winding itself. The stranded conductor is also more flexible than a solid conductor of similar size, aiding manufacture.[48]

For signal transformers, the windings may be arranged in a way to minimize leakage inductance and stray capacitance to improve high-frequency response. This can be done by splitting up each coil into sections, and those sections placed in layers between the sections of the other winding. This is known as a stacked type or interleaved winding.

Both the primary and secondary windings on power transformers may have external connections, called taps, to intermediate points on the winding to allow selection of the voltage ratio. The taps may be connected to an automatic on-load tap changer for voltage regulation of distribution circuits. Audio-frequency transformers, used for the distribution of audio to public address loudspeakers, have taps to allow adjustment of impedance to each speaker. A center-tapped transformer is often used in the output stage of an audio power amplifier in a push-pull circuit. Modulation transformers in AM transmitters are very similar.

Certain transformers have the windings protected by epoxy resin. By impregnating the transformer with epoxy under a vacuum, one can replace air spaces within the windings with epoxy, thus sealing the windings and helping to prevent the possible formation of corona and absorption of dirt or water. This produces transformers more suited to damp or dirty environments, but at increased manufacturing cost.[49]

Coolant

Cut away view of three-phase oil-cooled transformer. The oil reservoir is visible at the top. Radiative fins aid the dissipation of heat.

High temperatures will damage the winding insulation. [50] Small transformers do not generate significant heat and are cooled by air circulation and radiation of heat. Power transformers rated up to several hundred kVA can be adequately cooled by natural convective air-cooling, sometimes assisted by fans.[51] In larger transformers, part of the design problem is removal of heat. Some power transformers are immersed in transformer oil that both cools and insulates the windings.[52] The oil is a highly refined mineral oil that remains stable at transformer operating temperature. Indoor liquid-filled transformers must use a non-flammable liquid, or must be located in fire resistant rooms.[53] Air-cooled dry transformers are preferred for indoor applications even at capacity ratings where oil-cooled construction would be more economical, because their cost is offset by the reduced building construction cost.

The oil-filled tank often has radiators through which the oil circulates by natural convection; some large transformers employ forced circulation of the oil by electric pumps, aided by external fans or water-cooled heat exchangers.[52] Oil-filled transformers undergo prolonged drying processes to ensure that the transformer is completely free of water vapor before the cooling oil is introduced. This helps prevent electrical breakdown under load. Oil-filled transformers may be equipped with Buchholz relays, which detect gas evolved during internal arcing and rapidly de-energize the transformer to avert catastrophic failure.[42]

Polychlorinated biphenyls have properties that once favored their use as a coolant, though concerns over their environmental persistence led to a widespread ban on their use.[54] Today, non-toxic, stable silicone-based oils, or fluorinated hydrocarbons may be used where the expense of a fire-resistant liquid offsets additional building cost for a transformer vault.[50][53] Before 1977, even transformers that were nominally filled only with mineral oils may also have been contaminated with polychlorinated biphenyls at 10-20 ppm. Since mineral oil and PCB fluid mix, maintenance equipment used for both PCB and oil-filled transformers could carry over small amounts of PCB, contaminating oil-filled transformers. [55]

Some "dry" transformers (containing no liquid) are enclosed in sealed, pressurized tanks and cooled by nitrogen or sulfur hexafluoride gas.[50].

Experimental power transformers in the 2 MVA range have been built with superconducting windings which eliminates the copper losses, but not the core steel loss. These are cooled by liquid nitrogen or helium.[56]

Terminals

Very small transformers will have wire leads connected directly to the ends of the coils, and brought out to the base of the unit for circuit connections. Larger transformers may have heavy bolted terminals, bus bars or high-voltage insulated bushings made of polymers or porcelain. A large bushing can be a complex structure since it must provide careful control of the electric field gradient without letting the transformer leak oil.[57]

Applications

A major application of transformers is to increase voltage before transmitting electrical energy over long distances through wires. Wires have resistance and so dissipate electrical energy at a rate proportional to the square of the current through the wire. By transforming electrical power to a high-voltage (and therefore low-current) form for transmission and back again afterwards, transformers enable economic transmission of power over long distances. Consequently, transformers have shaped the electricity supply industry, permitting generation to be located remotely from points of demand.[58] All but a tiny fraction of the world's electrical power has passed through a series of transformers by the time it reaches the consumer.[27]

Transformers are also used extensively in electronic products to step down the supply voltage to a level suitable for the low voltage circuits they contain. The transformer also electrically isolates the end user from contact with the supply voltage.

Signal and audio transformers are used to couple stages of amplifiers and to match devices such as microphones and record player s to the input of amplifiers. Audio transformers allowed telephone circuits to carry on a two-way conversation over a single pair of wires. Transformers are also used when it is necessary to couple a differential-mode signal to a ground-referenced signal, and for between external cables and internal circuits.

Notes

1. ^ a b c Coltman, J. W. (January 1988), "The Transformer", Scientific American: 86–95, OSTI:6851152
2. ^ a b Stanley Transformer, Los Alamos National Laboratory; University of Florida, retrieved on 2009-01-09
3. ^ W. De Fonveille (1880-1-22). "Gas and Electricity in Paris". Nature 21 (534): 283. Retrieved on 2009-01-09.
4. ^ Hughes, Thomas P, Networks of Power: Electrification in Western Society, 1880-1930, The John Hopkins University Press, Baltimore and London, 1993. ISBN 0801846145, 9780801846144.
5. ^ a b Allan, D.J., "Power transformers – the second century", Power Engineering Journal
6. ^ Uppenborn, F. J., History of the Transformer, E. & F. N. Spon, London, 1889.
7. ^ U.S. Patent 352,105
8. ^ "Hungarian Inventors and their Inventions in the Field of Heavy-Current Engineering". energosolar.com. Retrieved on 26 December 2008.
9. ^ http://www.hpo.hu/English/feltalalok/blathy.html
10. ^ "Ottó Titusz Bláthy". Hungarian Patent Office. Retrieved on 26 December 2008.
11. ^ Skrabec, Quentin R. (2007). George Westinghouse: Gentle Genius. Algora Publishing. pp. 102. ISBN 978-0875865089.
12. ^ a b Flanagan, William M. (1993-01-01). Handbook of Transformer Design and Applications. McGraw-Hill Professional. Chap. 1, p. 1–2. ISBN 0070212910.
13. ^ a b Winders. Power Transformer Principles and Applications. pp. 20–21.
14. ^ a b c d Say, M. G. (February, 1984). Alternating Current Machines, Fifth Edition. Halsted Press. ISBN 0470274514.
15. ^ Heathcote, Martin (1998-11-03). J & P Transformer Book, Twelfth edition. Newnes. pp. 2–3. ISBN 0750611588.
16. ^ a b c d e Calvert, James (2001). "Inside Transformers". University of Denver. Retrieved on 2007-05-19.
17. ^ a b McLaren, P. G. (1984-01-01). Elementary Electric Power and Machines. pp. 68–74. ISBN 0132576015.
18. ^ Say, M. G. (February, 1984). Alternating Current Machines, Fifth Edition. Halsted Press. pp. 485. ISBN 0470274514.
19. ^ a b c Dixon, Lloyd, "Magnetics Design Handbook", Texas Instruments
20. ^ a b Billings, Keith (1999). Switchmode Power Supply Handbook. McGraw-Hill. ISBN 0070067198.
21. ^ "400 Hz Electrical Systems". Aerospaceweb.org. Retrieved on 2007-05-21.
22. ^ Kubo, T.; Sachs, H.; Nadel, S. (2001), Opportunities for new appliance and equipment efficiency standards, American Council for an Energy-Efficient Economy, pp. 39
23. ^ Riemersma, H., et al. (1981), "Application of Superconducting Technology to Power Transformers", IEEE Transactions on Power Apparatus and Systems PAS-100 (7): 3398, doi:10.1109/TPAS.1981.316682
24. ^ Calwell C. & Reeder T., (2002) Power Supplies: A Hidden Opportunity for Energy Savings NRDC
25. ^ a b c Heathcote, Martin (1998-11-03). J & P Transformer Book, Twelfth edition. Newnes. pp. 41–42. ISBN 0750611588.
26. ^ Pansini, Anthony J.. Electrical Transformers and Power Equipment. Fairmont Press. pp. 23. ISBN 0881733113.
27. ^ a b Nailen, Richard (May 2005), "Why we must be concerned with transformers", Electrical Apparatus
28. ^ a b c Daniels, A. R.. Introduction to Electrical Machines. pp. 47–49.
29. ^ a b Say, M. G. (February, 1984). Alternating Current Machines, Fifth Edition. Halsted Press. pp. 142–143. ISBN 0470274514.
30. ^ Pansini. Electrical Transformers and Power Equipment. pp. pp89–91.
31. ^ Bakshi, M. V. and Bakshi, U. A.. Electrical Machines - I. pp. 330. ISBN 8184310099.
32. ^ a b Kulkarni, S. V. and Khaparde, S. A. (2004-05-24). Transformer Engineering: design and practice. CRC. pp. 36–37. ISBN 0824756533.
33. ^ Say, M. G. (February, 1984). Alternating Current Machines, Fifth Edition. Halsted Press. pp. 166. ISBN 0470274514.
34. ^ Hindmarsh. Electrical Machines and their Applications. pp. p173.
35. ^ Abdel-Salam, M. et al.. High-Voltage Engineering: Theory and Practice. pp. pp. 523–524}. ISBN 0824741528.
36. ^ Carr, Joseph. Secrets of RF Circuit Design. pp. pp. 193–195}. ISBN 0071370676.
37. ^ Guile, A. and Paterson, W.. Electrical Power Systems, Volume One. pp. 330–331. ISBN 008021729X.
38. ^ Institution of Electrical Engineers. Power System Protection. pp. 38–39. ISBN 0852968345.
39. ^ a b Hindmarsh, John. Electrical Machines and their Applications. Pergamon. pp. 29–31. ISBN 0080305733.
40. ^ Gottlieb, Irving. Practical Transformer Handbook. Newnes. pp. 4. ISBN 075063992X.
41. ^ a b c d McLyman, Colonel Wm. T.. Transformer and Inductor Design Handbook. CRC. Chap. 3, pp. 9–14. ISBN 0824753933.
42. ^ a b Harlow, James H.. Electric Power Transformer Engineering. Taylor & Francis. Chap. 2, pp. 20–21.
43. ^ Boteler, D. H.; Pirjola, R. J.; Nevanlinna, H. (1998), "The effects of geomagnetic disturbances on electrical systems at the Earth's surface", Advances in Space Research 22: 17–27, doi:10.1016/S0273-1177(97)01096-X
44. ^ Hasegawa, Ryusuke (2000-06-02). "Present status of amorphous soft magnetic alloys". Journal of Magnetism and Magnetic Materials 215-216: 240–245. doi:10.1016/S0304-8853(00)00126-8.
45. ^ McLyman. Transformer and Inductor Design Handbook. Chap. 3 p1.
46. ^ Say, M. G. (February, 1984). Alternating Current Machines, Fifth Edition. Halsted Press. pp. 485. ISBN 0470274514.
47. ^ Lee, Reuben. "Air-Core Transformers". Electronic Transformers and Circuits. Retrieved on 2007-05-22.
48. ^ a b c Central Electricity Generating Board (1982). Modern Power Station Practice. Pergamon Press.
49. ^ Heathcote, Martin (1998-11-03). J & P Transformer Book. Newnes. pp. 720–723. ISBN 0750611588.
50. ^ a b c Kulkarni, S. V. and Khaparde, S. A. (2004-05-24). Transformer Engineering: design and practice. CRC. pp. 2–3. ISBN 0824756533.
51. ^ Pansini, Anthony J.. Electrical Transformers and Power Equipment. Fairmont Press. pp. 32. ISBN 0881733113.
52. ^ a b Willis, H. Lee (2004). Power Distribution Planning Reference Book. CRC Press. pp. 403. ISBN 0824748751.
53. ^ a b ENERGIE (1999) (PDF). The scope for energy saving in the EU through the use of energy-efficient electricity distribution transformers.
54. ^ ASTDR ToxFAQs for Polychlorinated Biphenyls, 2001, retrieved on
55. ^ McDonald, C. J. and Tourangeau, R. E. (1986). PCBs: Question and Answer Guide Concerning Polychlorinated Biphenyls. Government of Canada: Environment Canada Department. pp. 9. ISBN 066214595X. Retrieved on 2007-11-07.
56. ^ Pansini, Anthony J.. Electrical Transformers and Power Equipment. Fairmont Press. pp. 66–67. ISBN 0881733113.
57. ^ Ryan, Hugh M.. High Voltage Engineering and Testing. Institution Electrical Engineers. pp. 416–417. ISBN 0852967756.
58. ^ Heathcote. J & P Transformer Book. pp. 1.